For a few weeks running now, we have been covering the subject of multimode optic installations, something which used to be standard practice in very many 20-year old buildings. In those days, they were mainly of the OM1 (62,5/125) and OM2 (50/125) type, which were widely used at the time, for such purposes. So far, so good, if you consider that they were initially intended to work in network plans designed for speeds of up to 10 or 100Mbit only.
Even switching to 1G Ethernet, did not present much of a challenge either. Nowadays, due to increased pressures on bandwidth requirements to the net, all this has changed, specially in the case of Access Switches, now requiring 10G Ethernet for a smooth and efficient run. However, it is important to observe that the maximum distance achievable with OM1 and OM2 are of 33metres and 86metres, respectively.
For the purpose of this discussion, it would pay to make a mental note of these two figures whilst drawing up an imaginary plan of the inside of a building. You will very quickly come to the conclusion that we are talking about distances well over 100metres in length. This was often the case in the past, since fiber optic cables were always laid when the 90 + 10 metres were no longer attainable on Cat5.
Should you consult a manufacturer on how to solve this issue, the answer is always, annoyingly, the same:
’’If 10G is needed over 100metres, you need to lay OM3, or better still (please read here, better for the manufacturers), OM4 optical cables”! We did not want to leave these statements unchallenged since it is common knowledge that the replacement of fiber is an enormously time-consuming affair without even mentioning the subject of spiraling costs. This is why we decided to run some tests on these old optical cables to see whether we can break the OM2 86m sonic wall, using standard optics. Guess what? It worked!
Test configuration plans:
Which ‘’other’’ additional components were used in the installation?
What we did first of all, was to take a 10G XFP LR with 1310nm generated by a DFB Laser. This took us to the above-mentioned 640 meters! The 1700 were achieved by using 10G XFP ER at 1550nm.In addition to all of this, we also used a mode conditioning cable when coupling the laser.
The conclusion we should draw from this is that you should not always believe the cable lobby and that you should feel free to consult us at any time in the case of an infrastructure test run.
The entire thing was kindly supported by Dirk Spieß, a distinguished expert in the field of passive optical fibers. He spliced the distances and measured each and every single one with the help of his OTDR aid.
We helped our client by installing the 10LR optics. A link was established (after having stood idle for over 5 months!), 10G per second was achieved over the new distance! The manufacturer confirmed ‘’off the record’’ (unfortunately, we have nothing in writing to prove this conversation took place) that from 250 metres onwards, the use of singlemode fiber is recommended.